NEC code change for an engine-generator remote start circuit
There has been a recent change to the 2017 edition of the National Electrical Code for an engine-generator remote start circuit in an emergency system.
The differences between Indoor, Sprinkler-proof and Outdoor rated Pow-R-Way III Busway
Learn about the applicable conditions for busway installation.
The Short-Circuit WCR is the UL 1008 test for a transfer switch’s ability to close into and withstand a fault current. These are the ratings which will actually appear on the UL label of the product.
Eaton Dual-Sliding End of Row Doors Installation Video
Installation video for Eaton’s Data Center End of Row Doors.
The Tacoma Narrows Bridge was classic mechanical resonance. This video explains a similar problem with electrical systems when capacitors are applied with harmonic loads. At PSEC, we have a great demo to show series and parallel harmonic resonance.
Arc Flash Solutions
Arc flash part 2-arc flash solutions! Eaton's Power Systems Experience Center is the perfect place to see arc flash solutions in action including: arc quenching switchgear, ARMS, arc resistant switchgear, PX Dashboard, remote racking and many more!
Arc Quenching Switchgear at Eaton's Experience Center
Visit Eaton's Experience Center in Warrendale, PA to learn more about Arc Quenching Switchgear through an interactive demonstration. Seeing is believing.
Arc Quenching Switchgear video series: Ensuring the path of lowest impedance
In our final video, Adams explains how you can be sure that the current path created by the Arc Quenching Device is always going to be the one of lowest impedance, and therefore will extinguish any given arc fault inside the switchgear.
Arc Quenching Switchgear video series: Creating a low impedance current path
In our fourth video, learn how the Arc Quenching Device creates a current-limited, lower impedance current path to extinguish an arcing fault inside the switchgear.
Arc Quenching Switchgear video series: How the Arc Quenching Device works
In our third video, see the internals of the blue Arc Quenching Device and learn how it extinguishes an arcing fault in a total of 4 milliseconds without stressing the power distribution system.
Arc Quenching Switchgear video series: Recovering from an arc flash incident
In our second video, see Adams Baker explain how, in the event of an arc flash, AQS can be returned to service within hours. See what it takes to make this possible.
- Next Page